E are authorized as "S&A" brand name product agent. Ll of S&A water chillers are certified with design patent.
Its emitting rate is higher than 60%. Have design patent Certificate, CE and RoHS Certificate.
Economic cooling equipment, easy to install and operate, compact and easily movable. It is suitable for cooling the laser tube under 150W, and the temperature can be adjusted precisely. You can choose different models according to local voltage and frequency.It can extend the using life of laser tube and ensure the engraving effect better. With completed water flow and over high temperature alarm functions. It can control the water temperature, precision is ±0.3, which provide stable working conditions for laser devices. Multiple alarm function: compressor time-delay protection, compressor overcurrent protection, water flow alarm and over high / low temperature alarm. This series of water chillers adopt intelligent controller, which need not adjust the control parameters under normal. Circumstances, it will automatically adjust control parameters according to room temperature changes, to meet the cooling requirement. CW-5200 water chiller has unique low flow alarm protection function, which ensures the cooling water cycle working safely. Specific disconnection alarm securing protection. Enclosed water tanks, water used for a long time. Equipped with alarm output port, can quickly protect sensitive components.
High cost performance, low failure rate. Multiple power specifications; CE approval; REACH approval; RoHS approval.
Overcurrent protection for compressor, flow alarm, over temperature alarm. 58X29X47 cm (L X W X H). 70X43X58 cm (L X W X H). Independent production of sheet metal. High precision temperature control system.
Adopt IPG fiber laser for welding and cutting sheet metal. Temperature control accuracy can reach ±0.3. Ease of moving and water filling.The firm handle can help move the water chillers easily. Inlet and outlet connector equipped.
The laser will stop working once it receives alarm signal from the water chiller for protection purpose. Cooling fan of famous brand installed.
Adopt SAN JU cooling fan with high quality and low failure rate. Customized dust gauze available and easy to take apart. The new T503 intelligent temperature controller does not need to adjust the controlling parameters under normal circumstance. It will self-adjust controlling parameters according to room temperature for meeting equipment cooling requirements. User also can adjust the water temperature as needed.
Indicators D1, D2 (as shown) of thermostat working state D1 ON: thermostat works in intelligent control mode; D1 OFF: thermostat works in temperature control mode; D1 FLASHES: thermostat works in parameters setting mode or displays value of room temperature; D2 ON: chiller works in refrigerating state; D2 OFF: chiller works in the insulation working state; D2 FLASHES: chiller works in the energy-saving state. Press button will show the room temperature, 6 seconds later to display the restore defaults. Meanwhile, D1 is flashing, displaying room temperature. Keys are for adjusting the display status of the controller, parameters selection and adjustment. SET key: function setting key.
(1) Alarm Display: When alarm occurs, the error code and the temperature will be alternately displayed. (2) To suspend the alarm: In alarming state, the alarm sound could be suspended by pressing any button, but the alarm display remains until the alarm condition is eliminated. In order to guarantee the equipment will not be damaged while cooling water circulation is out of control, CW-5000/5200series chillers possesses an unique low flow alarm protection. (1) Flow alarm output ports and the wiring diagram.
(2) Flow alarm causes of circulating cooling water and working state. Note: The flow alarm is connected to the normally open relay and normally closed relay contacts, requiring operating current less than 5A, working voltage less than 300V. Chiller CW-5200 for 150W metal laser cutting machine Water chiller CW-5200 for acrylic co2 laser cutting machine Industrial chiller CW-5200 for laser cutter Air cooled chiller CW-5200 for co2 laser cutting & engraving machine Water cooled chiller CW-5200 for uv laser marking machine CW-5200 chiller for 8w-15w uv laser machine Refrigeration water chiller CW-5200 for laser marking machine Compressor water chiller CW-5200 for UV curing system printer Industrial water chiller CW-5200 for laser marker. Open the package to check if the machine is intact and all the necessary accessories are completed. Open the injection port to feed cooling water.Do not let the water spill over! Observing the water level gauge and adding water slowly, be careful not to have the water overflowed! For the cooling of carbon steel equipment, the water should be added an appropriate amount of cooling water additive (anti-corrosion water aqua). Working in cold north area, its better to use noncorrosive antifreeze fluid. According to system conditions, please connect the water inlet and outlet pipe well. Plug in power, turn on the power switch. Do not start up without water in the water tank!
(1) Power switch turned on, the circulation pump of the chiller starts working. The first time of operating may cause more bubbles in the pipe leading to a flow alarming occasionally, but running for a few minutes later, it will go back to normal. (2) After the first boot, you must immediately check whether the water pipe leaks. (3) Power switched on, if the water temperature is below the set value, it is normal that fans and other components of the machine do not work.The temperature controller will automatically control the working conditions of the compressor, magnetic valve, fans and other parts based on the set controlling parameters. (4) As it takes a longer time to start over the compressor and other components, according to different conditions, the time is range from seconds to minutes, so do not turn off the power and again on frequently. Check the water level in the water tank. The first startup of the new chiller empties the air in the water pipe, leading a slight water level decline, but in order to keep the water level in the green area, its allowed to add adequate water again. Please observe and record the current water level, and inspect it again after the chiller running for a period of time, if the water level drops obviously, please re-inspect the water pipeline leakage. Adjust parameters of temperature controller. CW-5000/5200 series use an intelligent thermostat. Normally users do not need to adjust it.
If it is really necessary, please refer to page 15, Operating status and parameters adjustment. Please ensure that the power supply and electrical outlet are in good contact and the earth wire must be firmly grounded! Please make sure there is stable and normal voltage for the working chiller! As the refrigeration compressor is more sensitive to the power supply and voltage, so the operating voltage of our standard product is of 210 240V (110V model is of 100 120V).
If you do need a wider operating voltage range, customization is available for us. Unmatched power frequency can cause the chiller damage!
Please choose model of 50Hz or 60Hz according to actual circumstance. To protect the pump, its strictly forbidden to run the chiller without water in the storage water tank! The new machine is packed after draining whole water in the tank, so please make sure the tank has water inside before machine starting, otherwise its easily to have the pump damaged.
When the water level is below the green (NORMAL) range of the water level gauge, the cooling capacity of our chiller will go down slightly. Hence please ensure the water level is within the green (NORMAL) range.To drain through circulating pump is strictly prohibited! Please be sure that the air inlet and air outlet are in good ventilation! There must be at least 30cm from obstructions to the air outlet which is in the back of the cooler, and should leave at least 8cm between obstructions and the side air inlet.
The filter screen must be regularly cleaned! Its essential to unpick and wash the dust gauze, or the serious blockage will cause breakdown to the chiller. Please pay attention to the effect of the condensate water!
With greater ambient humidity, when the water temperature is lower than the ambient temperature, the condensate water will generate on the surface of water circular pipes and the cooled components. If above circumstance appears, it is recommended to set a higher water temperature or keep pipes and cooled parts warm. The appliance is not to be used by children or persons with reduced physical, sensory or mental capabilities, or lack of experience and knowledge, unless they have been given supervision or instruction, children being supervised not to play with the appliance! Machine turned on but unelectrified.
Power cord is not plugged in place. Check and ensure the power interface and the power plug is plugged in place and in good contact. Pull out the fuse box from the power supply interface of the chiller, check the fuse, replace with spare fuse if necessary and check whether the power supply voltage is stable; Check and ensure the power interface and the power plug is plugged in place and in good contact. Flow Alarm (panel red light is on)use a water pipe directly connect to the water outlet and inlet but still without water flowing. Water level in the storage water tank is too low.Check the water level gauge display, add water until the level shown in the green area; And check whether water circulation pipe leaks. Flow Alarm occurs while running with other equipment (panel red light is on), but there is water flowing and no alarm when use a water pipe directly connected to the chiller water outlet and inlet. Water circulation pipes are blocked or a pipe bending deformation. Blocked dust gauze, bad thermolysis. Unpick and wash the dust gauze regularly.
Poor ventilation for air outlet and inlet. To ensure a smooth ventilation for air outlet and inlet. Voltage is extremely low or astable.
To improve the power supply circuit or use a voltage regulator. Improper parameter settings on thermostat. To reset controlling parameters or restore factory settings. To ensure there is sufficient time for refrigeration (more than 5 minuets). Reduce the heat load or use other model with larger cooling capacity.
Alarm for ultra-high room temperature. The working ambient temperature is too high for the chiller. To improve the ventilation to guarantee that the machine is running under 40. Serious problem of condensate water. Water temperature is much lower than ambient temperature, with high humidity.
Increase water temperature or to preserve heat for pipeline. Water drains slowly from outfall during water changing. Injection port is not open. The item "S&A CW-5200TH Industrial Water Chiller for 130-150W CO2 Glass Laser Tube Cooling" is in sale since Wednesday, November 18, 2020. This item is in the category "Business & Industrial\HVAC & Refrigeration\Other HVAC & Refrigeration".
The seller is "globalsigns16" and is located in Rowland Heights, California. This item can be shipped to United States, Canada, China, Mexico.